Applications Directly buried or installed in ducts for 600 volt secondary distribution. Construction Concentric stranded or compressed 1350-H19 aluminum conductor, crosslinked polyethylene insulation. Standards Secondary UD single conductor 600V cable meets or exceeds the following ASTM specifications. B-230 Aluminum Wire, 1350-H19 for Electrical Purposes. B-231 Aluminum 1350 conductors, Concentric-Lay-Stranded. B-786 "19 Wire combination unilay-stranded Aluminum Conductors for subsequent insulation". B-901 "Compressed round stranded Aluminum Conductors using single input wire construction". Secondary UD single conductor 600V cable meets or exceeds all applicable requirements of ICEA S-105-692. "USE-2" per UL 854 available upon request. Options Cable in Duct (CIC) Abrasion Resistant Ampacity 90oC conductor temperature, 20oC ambient, RHO factor 90, 100% load factor for three conductor triplexed, 3 phase operation. To determine correct ampacity by conductor size, please consult the National Electric Code, latest edition.
Image not available for
- Sorry, this item is not available in
- Image not available
- To view this video download Flash Player