Southwire Armorlite ® Type MC Cable is suitable for use as follows:
? Branch, feeder and service power distribution in commercial, industrial, institutional, and multi-residential buildings.
? Power, lighting, control, and signal circuits.
? Fished or embedded in plaster.
? Concealed or exposed installations.
? Environmental air-handling spaces per NEC 300.22 (C).
? Places of Assembly per NEC 518.4 and theaters per NEC 520.5.
? Installation in cable tray and approved raceways.
? Under raised floors for information technology equipment conductors and cables per NEC 645.5(D) & 645.5(D)(2).
? Class I Div. 2, Class II Div 2, & Class III Div. 1 Hazardous Locations.
STANDARDS & REFERENCES
Southwire Armorlite ® Type MC Cable meets or exceeds the requirements of the following
? UL 83
? UL 1569
? UL 1685
? Federal Specification A-A59544 (formerly J-C-30B)
? FT4/IEEE 1202 (70,000 Btu/hr) Vertical Cable Tray Flame Test
? Listed for use in UL 1, 2 and 3 Hour Through Penetration Firestop Systems
Southwire Armorlite ® Type MC Cable is constructed with soft-drawn copper, Type THHN/THWN conductors rated 90°C dry
available in sizes 14 AWG through 2 AWG, and a green insulated grounding conductor. The conductors are cabled together
and a binder tape bearing the print legend is wrapped around the assembly. Aluminum interlocking armor is applied over the