|Part Number||SER CUF|
|Material||copper, polyvinyl chloride|
50' 3-3-3-5 SER Copper Service Entrance Wire Cable
|Price:||$419.21 & FREE Shipping|
Customers who viewed this item also viewed
Have a question?
Find answers in product info, Q&As, reviews
Please make sure that you are posting in the form of a question.
Compare with similar items
USE, Underground Service Entrance Cable
378’ 2-2-2-4 SER Copper Service Entrance Wire Cable
150' Aluminum URD Dyke 2-2-2-4 Cable Direct Burial Quadruplex Secondary Wire
100' ALUMINUM 2-2-2 Triplex URD Ramapo 100 AMP Direct Burial Wire Service Cable
50' 2/0-2/0-2/0-1 SER WG Aluminum Service entrance Cable Wire
|Shipping||FREE Shipping||FREE Shipping||FREE Shipping||FREE Shipping||FREE Shipping||FREE Shipping|
|Sold By||Nassau National Cable Co.||Great Household||Nassau National Cable Co.||Nassau National Cable Co.||Nassau National Cable Co.||Nassau National Cable Co.|
|Size||50 ft||4 AWG||378FT||150 ft||100 Feet||50 ft|
Applications: Southwire Type SE, service entrance cable is primarily used to convey power from the service drop to the meter base and from the meter base to the distribution panelboard; however, the cable may be used in all applications where Type SE cable is permitted. SER may be used in wet or dry locations at temperatures not to exceed 90°C. Voltage rating is 600 volts. STANDARDS & REFERENCES: Southwire Type SE cable meets or exceeds UL Standard 44 for XHHW-2 conductors or UL 83 for THHN/THWN conductors, UL Standard 854, Federal Specification A-A-59544, and requirements of the National Electrical Code1. CONSTRUCTION: Southwire Type cable is constructed with sunlight resistant Type XHHW-2 conductors or Type THHN/THWN conductors. Copper conductors are annealed (soft) copper. Cable assembly plus reinforcement tape are jacketed with sunlight resistant gray polyvinyl chlo- ride (PVC). Available as 1 conductor with a concentric ground, 2 conductor with a round or concentric ground, or 3 conductor with a bare ground. SE cable is jacketed with gray sunlight resistant polyvinyl chloride (PVC). SPECIFICATIONS: Cable shall be UL-listed Type SE, Style U, suitable for operation at 600 volts or less in all installations as specified in the National Electrical Code. Conductors shall be annealed copper, Type XHHW-2 or Type THHN/THWN, weather resistant PVC jacketed, as manufactured by Southwire Company or approved equal. Order Carefully No Returns.
|5 star (0%)|
|4 star (0%)|
|3 star (0%)|
|2 star (0%)|
|1 star (0%)|