Other Sellers on Amazon
+ Free Shipping
+ Free Shipping
+ Free Shipping
CyberPower CP1500PFCLCD PFC Sinewave UPS System, 1500VA/900W, 10 Outlets, AVR, Mini-Tower
- Enter your model number to make sure this fits.
- 1500VA/900W PFC Sine Wave Battery Backup Uninterruptible Power Supply (UPS) System - designed to support Active PFC and conventional power supplies
- 10 NEMA 5-15R OUTLETS: (5) Battery Backup & Surge Protected Outlets, (5) Surge Protected Outlets safeguard servers, workstations, network devices and telecom equipment. The UPS also includes 2 USB charge ports (1 Amp shared) to power portable devices
- MULTIFUNCTION LCD PANEL: Displays immediate, detailed information on battery and power conditions, including: estimated runtime, battery capacity, load capacity, etc.
- AUTOMATIC VOLTAGE REGULATION (AVR): Corrects minor power fluctuations without switching to battery power, thereby extending the life of the battery
- 3-YEAR WARRANTY – INCLUDING THE BATTERY, $500,000 Connected Equipment Guarantee and FREE PowerPanel® Personal Edition Management Software (Download)
|Special Shipping Information: This product may not be available for 1 or 2 day shipping due to federal regulations that require it to ship via ground ship methods only. This product can only be shipped within the 48 contiguous states.
Frequently bought together
Customers who bought this item also bought
Have a question?
Find answers in product info, Q&As, reviews
Please make sure that you are posting in the form of a question.
From the manufacturer
- Capacity: 1500VA / 900W
- Topology: Line Interactive
- Waveform: Sine Wave
- Plug type & cord: NEMA 5-15P, 5 ft. cord
- Outlet types: 10 × NEMA 5-15R
- Communication: USB, Serial
- Data line protection: Telephone, Ethernet, Coaxial
The CyberPower CP1500PFCLCD provides battery backup and surge protection
For PCs and other electronics
A desktop UPS with line interactive topology, this CyberPower PFC Sinewave UPS provides battery backup, power protection (using sine wave output), and surge protection for desktop computers, workstations, networking devices, and home entertainment systems requiring Active PFC power source compatibility. The UPS uses Automatic Voltage Regulation (AVR) to correct minor power fluctuations without switching to battery power, which extends battery life. AVR is essential in areas where power fluctuations occur frequently.
- What's in the Box (1) UPS system; (1) User manual, (1) USB A+B type cable; (1) Telephone cable; (1) Coaxial cable; (1) Function Setup Guide, and (1) PowerPanel Personal Edition software CD
- Management software: PowerPanel Personal Edition
- ENERGY STAR qualified
Why You Need It
When power goes out for even a second it can result in data loss and hardware damage which can shorten equipment life expectancy. This battery backup unit provides sufficient emergency runtime power to allow for safe closure of open files and proper shut down of electronics when an outage occurs. In addition, it safeguards electronics from commonly occurring power surges caused by storms, activity on the power grid, or high-powered equipment turning on and off.
Provides backup power and surge protection for home and small office computers, wired and wireless network routers and modems, home theater systems, game consoles, and personal electronics. Safeguards valuable documents, photos, videos, and music files from loss or damage due to power fluctuations and surges as well as uncontrolled equipment shutdown caused by power interruptions.
Power Management Software
PowerPanel Personal Edition software is available free for download with all UPS systems with a USB or serial port. The software features a user-friendly dashboard interface for controlling and monitoring a CyberPower UPS systems. Its advanced functionality includes; runtime management, self testing, event logging and more.
|Battery Backup with Surge Protection||✓||✓||✓||✓||✓|
|Automatic Voltage Regulation (AVR) - Line-Interactive Topology||✓||✓||✓||✓||✓|
|Pure Sine Wave Waveform - Active PFC Compatibilty||✓||✓||✓||✓||✓|
|Free Automatic Shutdown Software with USB Connectivity||✓||✓||✓||✓||✓|
|Network DSL Phone (RJ11/RJ45) Surge Protection||✓||✓||✓||✓|
|Coaxial (RG6) Surge Protection||✓||✓||✓||✓|
Compare to similar items
|Shipping||FREE Shipping||FREE Shipping||FREE Shipping||FREE Shipping||FREE Shipping||FREE Shipping|
|Item Dimensions||3.9 x 14.2 x 10.4 in||4 x 13.25 x 9.75 in||4.41 x 14.96 x 11.85 in||4.13 x 10.79 x 5.47 in||3.9 x 14 x 11 in||17 x 15.3 x 3.5 in|
|Item Weight||24.7 lbs||25 lbs||26.68 lbs||7.5 lbs||25 lbs||55.5 lbs|
The CyberPower CP1500PFCLCD PFC Series UPS with Pure Sine Wave output safeguards mid to high-end computer systems that use conventional and Active Power Factor Correction (PFC) power supplies. Its automatic voltage regulation (AVR) topology delivers clean and consistent AC power. Its patented GreenPower UPS advanced circuitry reduces UPS energy costs by up to 75% compared to competitive models. The CP1500PFCLCD has a capacity of 1500VA/900Watts, (10) NEMA 5-15R receptacles and (2) maintenance-free, user-replaceable 12V/8.5Ah batteries. The intelligent multi-function LCD panel displays real-time UPS vitals for ease of control. Connectivity via (1) HID USB and (1) DB9 serial ports. Surge Protection for RJ11/RJ45 amp; coax. Two 5Vdc USB 2.0 charging ports for portable devices. PowerPanel Personal Edition UPS Management software, a standard Three-Year Warranty and a $500,000 Connected Equipment Guarantee are included.
Top customer reviews
There was a problem filtering reviews right now. Please try again later.
My first impression upon opening the cleverly double-boxed packaging was that the picture size was deceiving. This CyberPower looks large. It's not. It's dwarfed by my standard mid-ATX towers. Eyeballed relative to one, it's about half the width, half the height, and two-thirds the depth. Positively petite for a tower UPS and roughly the size of the APC it replaced were that one upturned. Extras include a short coaxial cable and an RJ-11 phone wire. Build quality seems quite good, with an attractive combination of gloss and matte black plastic. Once booted, the UPS is completely silent with mains power. It buzzes quietly and runs a small, audible internal fan when on battery.
That said, let's drill down the major features of the PFC series:
Line-interactive - In the consumer world, there are three major types of UPS units: standby, line-interactive, and double conversion ("online"). Standby runs wall power straight to the device with minimal filtering unless it detects a major voltage change. Then it switches to battery. Line-interactive is the same, except with a filtering transformer between the wall and the device to handle most voltage variations. In an area with dirty power, line-interactive units won't cycle to battery power as often. With clean power, there's no practical difference between the two. Double-conversion means the battery always powers the device and wall power only charges the battery. The isolation is helpful for sensitive things, but less efficient because the wall power is perpetually converted from AC to DC and back to AC. The heavy-duty inverter this type requires also tends to increase cost and noise.
Some areas will have greater voltage fluctuation than others. If you're in California and surrounded by industrial machinery, line-interactive or double-conversion is where you want to be.
Sine wave - When a UPS with this feature is on battery power, the cycling frequency of the AC it produces will be a smooth sine wave instead of a blocky approximation. (The quality of this approximation scales with price; the inverters in cheaper UPS models tend to produce pretty ghastly waveforms.) Most devices don't care. Some with a direct current path may, as will electric motors and instruments that derive their timing from the power frequency. The majority of computer power supplies will work fine with any UPS, but those with active power factor correction may turn off if they encounter a particularly poor sine approximation. If the system continues to run after the UPS switches to battery, and it probably will if it's older or inexpensive, you're in the clear. Pure sine output is compatible with all computers and skirts the issue entirely.
This UPS has a capacity of 600W and 1000VA. You can ignore the second number if your hardware is recent or expensive. In the grand old days when the real power use of a computer (W) was 40% less than the apparent load to the power grid (VA), it made sense to specify more VA capacity than W. Now, though, with power factor correction (an attempt make the ratio of W:VA closer to 1:1) standard for years, the actual load is likely to be 90% or more of the apparent load. A 200W computer will probably use 200-225VA of capacity. You're therefore likely to reach the watt limit well before the one for VA.
Here's how the PFC models compare in maximum capacity, battery size, and runtime:
CP850: 510W max, 1 x 7 amp-hours = 8 min @ 255W, 2 min @ 510W
CP1000: 600W max, 1 x 9 amp-hours = 9 min @ 300W, 3 min @ 600W
CP1350: 810W max, 2 x 7 amp-hours = 9 min @ 405W, 3 min @ 810W
CP1500: 900W max, 2 x 8.5 amp-hours = 11 min @ 450W, 2 min @ 900W
While the latter two have USB charging ports and more physical size to accommodate an extra battery, all four otherwise share the same feature set.
Runtime doesn't scale linearly with load. A CP1500 feeding 100W may well last 60 minutes. At 900W, it'll last 2 minutes, best case. That's a factor of 30 difference in runtime for only 9 times more load. To ensure your system stays on long enough to shut down properly, the expected draw shouldn't be more than about 70% of the maximum capacity. CyberPower's software can be configured to automatically shut down any single system via USB or serial, though the comments attached to this review note that older versions may write excessively to SSDs.
In my case, I've got a 12-drive file server, tower PC, router, switch, 24" LCD, and 32" LCD plugged in. The front-panel UPS LCD tells me that is an idle load of about 340W and 350VA. Projected runtime on my CP1000 is 6 minutes. A typical single computer and LCD monitor will draw 125W together. Gaming systems and larger screens, perhaps 150W-250W at idle. Most people with one system will find the CP850 adequate if they shut down soon after saving open work. Multiple systems or attempting to ride out a power loss would benefit from the CP1350 or above.
So how does the CP1000 perform? It's hard to say. It feels satisfyingly heavy even without the battery, but as I haven't torn it apart, it could well be filled with peanut brittle. There haven't been any lightning strikes, so the 1,030 joule surge rating (three times APC's typical rating) remains untested. Actually, the only stressor has been my laser printer. It's plugged into the same wall socket and when it heats up, the lights flicker and the UPS trips.
The switchover time from mains to battery isn't quite as fast with this Cyberpower. I know that because my APC caused a slight flicker on my LCD TV. This one gives a severe flicker that all but turns the TV off, though the other screen and the rest of the computer equipment are unaffected. It's also intolerant of overloads. Because a laser printer can easily pull 1200W or more, you're not supposed to plug one into any UPS outlet, battery-backed or not. I did by accident when I was moving cables around. The resulting shutdown and angry beeping was unsurprising. No docked stars for any of this, though I might have if the TV had actually turned off.
One niggle of note: my UPS took an usually long time to get past the initial startup. I spent about ten minutes pressing and holding buttons in accordance with the manual before it finally turned on. Since then, no similar issues, and I was alerted in a comment that it's possible to force the display to stay on by pressing and holding the display button until you hear a single beep.
All considered, I'd give this CyberPower a preliminary five stars. The APC lasted four years on the battery and five until the USB monitoring port went out, so that's the benchmark I hope it'll beat.
I recently had an extended power outage. The estimated runtime was nine minutes at the start, but the UPS shut off in four or less even with a smaller load than above. This is significantly below Cyberpower's projections for this unit, so I'm docking a star. I would be tempted to choose a CP1500 if I were buying again. They come on sale for $150 or so every few months.
I've had a new issue where the UPS stops powering all outlets for a few seconds at a time. No beeping or error messages ensue, but naturally, all devices turn off. The warranty for this unit is 3 years. Support has advised me to RMA. I'll update when that process is complete. Shipping to CyberPower was $18 through UPS. It's a very heavy package because they advise leaving the battery in.
CyberPower has shipped me what appears to be a new unit. Turnaround time was a little over a week. No UPS signature was required. I didn't have any trouble turning this one on.
No new issues to report. The replacement runs exactly as the original once did, recently powering my equipment during an Irma-related outage and automatically shutting down my server. Cyberpower has overhauled the monitoring application to be much more capable.
If you have a modern computer and it won't work with the cheaper UPS backup supplies when the power fails it is most likely because your computer has a PFC type power supply which WILL NOT WORK on any type of waveform other than a pure sine wave!
Some people complain that they wish the battery capacity was higher so they can run on battery power for tens of minutes if not an hour but the purpose of ANY UPS in this catagory is to allow the user to safely close their open files and shut down the computer in a matter of a few minutes, not power it for tens of minutes or longer. If you need extended time emergency backup power then you'll need either a backup generator or a bank of batteries running an inverter to supply power to your load.
I have posted a photo of the sine wave output from my CyberPower CP1350PFCLCD PFC Compatible 1350VA 810W UPS when it's running on battery power only and supplying about 175W to 200W of power to my computer and monitor. The waveform was smooth and actually had less distortion than what is coming out of my wall outlet!
Unlike some reviews from a year ago, there was no smell coming from the unit when I unpacked it and no smell when running so if that was a problem in the past they must have fixed it.
The only thing I wish were different is the lack of ability to keep the display backlight on (it goes off after several seconds when the front panel button is pushed - probably to save energy).
I highly recomend this product - especially if you are looking for a UPS that produces a true sine wave output for your computer's PFC power supply requirement.
May 21, 2012 - This is a follow up to my original posting. The UPS is still running great and I got a response from the manufacturer about how to keep the display light on constantly. "You can configure the LCD to stay ON at all times by pressing the DISPLAY button for 2 seconds until you hear a short beep. This will configure the display to stay on at all times."
CyberPower CP1350PFCLCD PFC Compatible 1350VA 810W Pure Sine Wave Tower UPS
-great value for money, in terms of battery capacity, feature set, power factor correction, and total efficiency.
-worked great for me for 4 solid years.
-convenient USB ports for charging portable devices without occupying outlets.
-Failed suddenly, unexpectedly, and not due to a battery fault. Unit was under idle load only at the time.
-Failure core F03 apparently means "warranty replacement only, do not attempt repair"
-CyberPower support did not provide any additional information, resources, parts, or labor. They would not repair the unit even if I paid for it.
-weird brownish-red goo near capacitors suggests that at least one capacitor has failed. Generally, replacing those caps is quick and cheap, and results in a fully operational unit.
-I don't like the idea of throwing away a current model product. This unit is likely very fixable. Even if they were to replace just the entire mainboard, the most expensive components (Transformer and Batteries) are fine. Total cost of repair might be $100 but that's less than a replacement unit.
I contacted CyberPower about it, and they said it wasn't under warranty anymore, so I should discard it. It's an expensive piece of equipment, which likely has $2 worth of parts to replace. It's extremely uncool to throw away a unit full of heavy metals and functional components over a dead cap.
I'd like to fix it, whether or not they want to help me. But I'm disappointed that they didn't offer and refused my first request for assistance.
Most recent customer reviews
Original Post - November 12, 2017 (Purchased November, 2016)
I bought this...Read more
I have non sine wave that kick in all the time and than light up the display ,but this...Read more