Other Sellers on Amazon
+ Free Shipping
+ $4.79 shipping
ICM Controls ICM253 Fan Delay Timer, 12-390 seconds Adjustable Off Delay
Get free shipping
Free 5-8 business-day shipping within the U.S. when you order $25 of eligible items sold or fulfilled by Amazon.
Or get 4-5 business-day shipping on this item for $5.99. (Prices may vary for AK and HI.)Learn more about free shipping
Fulfillment by Amazon (FBA) is a service we offer sellers that lets them store their products in Amazon's fulfillment centers, and we directly pack, ship, and provide customer service for these products. Something we hope you'll especially enjoy: FBA items qualify for FREE Shipping and Amazon Prime.
If you're a seller, Fulfillment by Amazon can help you increase your sales. We invite you to learn more about Fulfillment by Amazon .
Specifications for this item
|Brand Name||ICM Controls|
|Number of Items||1|
Frequently bought together
Customers who bought this item also bought
Customers also shopped for
Have a question?
Find answers in product info, Q&As, reviews
Please make sure that you are posting in the form of a question.
From the manufacturer
ICM Controls is a leading, ISO Certified manufacturer of electronic controls specializing in the HVAC industry. We have achieved this position through product and process innovation that spans more than 30 years, and we strive to maintain this position through extensive capitalization, focusing on our greatest manufacturing strength: true vertical integration. Our products are proudly made in America.
ICM Controls OEM Replacement
ICM282A Furnace Control - with software for enhanced controls operation in counter flow and down flow furnace applications. Replacement for OEM models including Carrier HK42FZ0-xx series control boards.
- Controls gas valve, ignitor, blower motor, inducer, humidifier and air cleaner
- Microprocessor-based precision
- Software for enhanced controls operation in counter flow and down flow furnace applications
- Designed for 100% gas shutoff in case of ignition failure
- Low cost form, fit and functional replacement board for Goodman, Janitor, TI, White-Rodgers and UTEC
- Microprocessor based design for precise timing
- Functions with all 24 VAC thermostats
- Diagnostic fault codes (blinking LED) for simple troubleshooting
- Twining compatible with another ICM280
Delay on Break Timer
Compressor lockout/Anti-Short cycle timer helps to protect compressors from damage caused by rapid short cycling simple, 2-wire hookup adjustable timing universal voltage. made in United States. Manufactured by ICM Controls.
Compressor lockout/anti-short cycle timer, Helps to protect compressors from damage caused by rapid short cycling. Simple, 2-wire hookup. Adjustable timing. Universal voltage.
Furnace Control Replacement
Furnace Control - Replacement For Oem Models Including Carrier Ces0110057-Xx Series Control Boards. Low Cost Form, Fit And Functional Replacement Board For Carrier Ceso11005700/01/02. Controls Gas Valve, Ignitor, Blower Motor, Inducer, Humidifier And Air Cleaner. Secondary Brownout Voltage Protection.
Diagnostic Fault Codes (Blinking Led) For Simple Troubleshooting. Made in United States. Manufactured by Icm Controls.
- Microprocessor-Based For Precise Timing
- Functions With All 24 Vac Thermostats
- Designed For 100% Gas Shutoff In Case Of Ignition Failure
- Twinning compatible with another ICM281 board
- Reverse polarity protection
Fan Blower Control OEM Replacement
Fan Blower Control - replacement for OEM models including Carrier CES0110017/18 and HH84AA-x series control boards. Specifically designed to replace popular gas furnace centers, Pin selectable blower delays. High power, relay output, Dual function fan delay timer, Controls the circulating fan in heat pump, A/C and forced air systems.
Post-purge fan delay timer with adjustable 12-390-second time delay.
Would you like to tell us about a lower price?
Top customer reviews
There was a problem filtering reviews right now. Please try again later.
My only complaint is that while it came with a small wiring diagram about the size of a business card- there really isn't much documentation at all. To be fair, I installed it correctly the first time, but I'm also pretty handy when it comes to electronics (I design PCB's and custom electronics as a hobby) so I'm probably not the average person trying to install this sorta thing. That said, there is enough information to get it to work- you just have to have a basic understanding of what you're doing.
I will say the diagram on the unit, which shows internal function, didn't make much sense. The switch shown in the diagram as going to terminal 4 makes better sense to me if it was showing to terminal 1, which is the load terminal (goes to fan relay). Just use the diagram on the paper that comes with it. (transformer wired across terminals 2 & 3 - be sure to match polatrity, thermostat to 4 and load on 1)
I set mine to about 2 minutes after the thermostat cuts off the A/C.
Like the diagram on the ICM253 unit.
--1 and 4--bypass (undo and reconnect) the current GREEN wire from the Fan (1) and the GREEN wire from the thermostat (4)
--2 and 3--tap (add into existing) into the 24vac from the RED (2) and BLUE/common/neutral (3) wires
I did not see the BLUE/COMMON/NEUTRAL 24vac wire once the furnace was opened.
The wire diagram makes no sense at all !!!
Google and YouTube did not help.
So I removed the two screws and take out the cover that protected/covered the wirings and the 24v transformer (besides the breakers).
I look for the 24v transformer and its Common/Neutral wire---It has wires out for the 24vac and wires in from the 240vac (labeled on the transformer...see picture).
I saw the 24vac Common/Neutral wire (gray colored on this wire).
I also saw that it was connected to the condenser outside...I simply tapped into that gray colored wire and done.
Hope it helps someone out a bit.
Have a great day.
So I installed this little gem on my furnace and set it for its stated maximum of 390 seconds. (The actual delay it delivers is closer to 410 seconds, but I’m not going to quibble.)
This relay does exactly what I expected it to do, and at a very attractive price point.
The main benefits to me in the dry Colorado climate are:
- increases humidity in the house during the cooling season (since much of the humidity remaining on the coil at the end of the cycle is returned to the house instead of going down the drain)
- dries the evaporator coil after each cooling cycle making it less likely to get moldy or grow bacteria
- improves efficiency of the A/C by extracting more cooling from the electricity used.
Wiring was pretty straightforward (but I’m an engineer). The device is installed in series between the G (fan) wire coming from your thermostat and the G terminal on your furnace, but also needs Common and Hot 24 volt connections from the furnace. It also requires the use of “disconnect F” quarter-inch tab connectors and a crimper.
Unless you are already skilled with low-voltage furnace wiring or really good at reading wiring diagrams, to avoid damaging your furnace or yourself, I recommend you get a pro (or a skilled friend) to help with the install.
The problem is when the person presses the button and releases shorter than say 2 seconds this relay does not pick it up. One has to hold the button for at least 3 seconds for it to pick up and activate the strobe light. I guess I can live with that by adding a sign at the door to hold the button for 3 seconds or more.